The sectional panel tank shall consist of 4' x 4' or 1 meter x 1 meter panel manufactured from 2.5mm to 4.0mm thickness according to requirement.
The sectional panels shall be pressed to double flanges at the angles of 45 degree and 90 degree to the face of the plate on four sides.
1.3 Reinforcement Method
All tanks are internally braced with angle stays to endure the rigidity of the tank when filled with the water.
The Top panel is supported by top panel support, which shall be made of stainless steel grade 304 or 316 material according to requirement
2.1 Bolt. nut & washers
i) All bolt, nut & washer in contact with water contained within the tank shall be of stainless steel conforming to AISI 316/304.
ii) All bolt, nut & washer for the tank external flanges are stainless steel 316/304.
2.2 Sealing material
Non-toxic P.V.C foam tape shall be used in between the joints.
The tank cover shall be constructed from 1.4mm to 3.0mm of thickness stainless steel AiSI 316/304 material according to the requirement.
2.4 Ladders and Level Indicator
Internal & external ladder shall be made of stainless steel grade 316/304 . Ladder indicator shall be made of Aluminium materal.