The sectional panel tank shall consist of 4' x 4' or 1 meter x 1 meter panel manufactured from 4.5mm to 6.0mm thickness according to requirement.
The sectional panels shall be pressed to double flanges at the angles of 45 degree and 90 degree to the face of the plate on four sides.
1.3 Reinforcement Method
All tanks are internally braced with angle stays to endure the rigidity of the tank when filled with the water.
The Top panel is supported by top panel support, which shall be made of hot-dipped galvanised material.
2.1 Bolt. nut & washers
hot-dipped galvanised material.
2.2 Sealing material
Non-toxic P.V.C foam tape shall be used in between the joints.
The tank cover shall be constructed from 1.4mm to 3.0mm of thickness hot-dipped galvanised material according to the requirement.
2.4 Ladders and Level Indicator
Internal & external ladder shall be made of hot-dipped galvanised material. Lavel indicator shall be made of Aluminium c/w P.V.C ball float.